Click here for pdf version.
Note: Set compatibility before removing battery pull tabs.
Remove backplate. Turn compatibility dial with flathead screwdriver to coordinating security system. See Figure A.
|Qolsys | Interlogix||2|
Mounting Location: The sensor should be mounted between 6.5ft and 8.5ft above the floor. All protected glass must be within a clear line of sight of the sensor and within the 20ft max range.
Note: For UL/cUL listed the device shall be secured using the provided mounting screws.
Remove back plate by prying top notch with a flathead screwdriver. See Figure B.
Note: To properly test the Versa Glass Break, a glass break simulator is required.
Sensitivity: Two dip switches allow you to customize the sensitivity and detection range of the Versa Glass. The factory default is set to MAX. Please refer to the table below to customize the sensitivity.
Switches: Set dip switches based on desired detection range.
Test Mode: Place the sensor in test mode by disconnecting the batteries for 30 seconds then reconnecting. Test mode is active for 5 minutes upon the sensor powering on. The LED blinks every second when the sensor is in test mode. The Versa Glass does not transmit an RF Signal while it is in test mode. Please refer to the table below for the LED indicator guide. The sensor will exit test mode after the first 5 minutes of power up.
|Initial Power Up||Rapid Flash For 5 Minutes|
|Test Mode||Flash Once Per Second|
|Test Mode, Alarm Event||Rapid Flash For 2 Seconds|
|Normal Mode, Alarm Event||Solid For 5 Seconds|
|Low Battery||Flash Once Every 30 Seconds|
Note: Serial numbers are located under battery. See Figure F.
This device complies with FCC Rules Part 15. Operation is subject to the following two conditions:
Changes or modifications not expressly approved by Versa Wireless Inc. can void the user’s authority to operate the equipment. Le présent appareil est conforme aux CNR d'Industrie Canada applicables aux appareils radio exempts de licence. L'exploitation est autorisée aux deux conditions suivantes : (1) l'appareil ne doit pas produire de brouillage, et (2) l'utilisateur de l'appareil doit accepter tout brouillage radioélectrique subi, même si le brouillage est susceptible d'en compromettre le fonctionnement.
¹ For UL compliance the units are for residential use only.